0115 775 0284Courtyard Business Centre, 41a Southwold Drive, Nottingham NG8 1PA Open 8.30am to 6.30pm
Nottingham Surveyors CPR 35 Report on a poorly constructed Nottingham extension for Legal Proceedings
View of the half constructed Orangery
The pad stone for the lintel is out of plumb
The concrete has been poured around the radiator pipes without a protective sleeve. Concrete can attack the copper pipe causing a leak. It is particularly important to sleeve copper gas pipes or lay them in an inert material.
Thin concrete foundation poured on ground that has not been properly dug out. High risk of differential settlement causing cracks
The floor has been laid at the wrong level so a slope has been incorporated to get it down to the level of the French windows
Structural timbers have been screwed rather than bolted to the house wall
The block wall can be moved by pushing with your hand
Unsightly blocks projecting beyond the conservatory frame
Supposed channels for underfloor heating. The are to widely spaced. It is hard to imagine how the floor can be insulated to prevent loss of heat to the substructure.